.Not looking for a sync switch. I don't think the MEP803 are capable of sycn. operation. Yes they will. After all, the sync gear is NOT on the gen set. Its in the box. If you have the switch over box that would fit, for insistence the AN/MJQ-37 and -38, (or another museum piece like yours)You could do just what you want. There are several other PP, (Power Plants) that use this box. They are on the market. You didn't ask what would work, just if the switches you asked about, would be interchangeable. That box you wanted to use, is probably older then you! If you want a list of NSN's and part numbers, can do. Might take a few days, but the info is here. I can give you a parts listing and schematic so you can build your own if you want.
Just thinking of an Gen A to Gen B change over (as for maintenance). The switch I have on hand came from a MEP002 based Power plant and Guy says does not have capacity to handle 10kw. If can't find a switch it is not a huge deal. if the shelter/church goes dark for a 1/2hr while service genset that would be acceptable. My thinking is to mount 2x MEP803 and a 350gal fuel tank on an M702 dolly (that has a long frame). Have all on hand except a suitable A-B switch.
MEP at rating of 10kw is likely a bit small but need single phase. Have to live within the limitations of what DOD surplus has available.
Gen will supply 1ph to a 400a SquareD manual transfer switch I got from DOD surplus. Transfer switch to mount next to existing elec meter on building ext. Over kill on capacity but was no cost thru the DOD surplus program to FD (what was available for free). List price on the transfer switch is something like $13000. Doing the same install at our fire station.
I just rvcd a local grant to pay for install cost.
We get it, advertisements are annoying!
Sure, ad-blocking software does a great job at blocking ads, but it also blocks useful features of our website like our supporting vendors. Their ads help keep Steel Soldiers going. Please consider disabling your ad blockers for the site. Thanks!